The Points to Take Into Consideration in Manual Boilers
GENERAL INFORMATION REQUIRED TO TAKE INTO CONSIDERATION
The cleaning of exterior surface must not be made by sharp tools and chemical materials, it is best to clean it by warm water and soap.
Do not open the lids and keep them closed when the fire burns.
Do not spill your fuel with meltic plastic materials such as sack and bag. These may damage moving grid mechanism.
Make sure that the fuel is clean. Do not use wet and humid coal.
Do not ever use your boiler with the assembly connected by closed expansion. Warn your assembler.
If your flue draws very well, adjust flue valve.
The degree of boiler may increase and boiler may evaporates due to unadjusted valves.
Pay attention to perform operation of pumping water to the boiler when the boiler is cold.
During pumping water to boiler, drain the hose for a while because the air in the hose damages the system.
Do not lose instruction book, when reqired, we recommend you to take advantage of it again.
The compliance with the points specified in instruction book extends the efficiency and life of your boiler.
Use your boiler as our authorized service makes the arrangements and explains the use of the boiler which is delivered in working condition and do not play with the adjustments of your boiler except for knowledge of the service.
After the device is connected according to the instructions and the water is pumped to the installement, the first operation of the device should be asked for and the nearest Authorized Service of Yağmur Teknik should be reported by the assembler company.
Take your fuel prior to calling the service for the first operation.
Do not evacuate of installement while the pump is on.
Note that the quality of the fuel you will use will directly affect the efficiency of boiler, quality of burning, amount of ash and cleaning periods and amount of fuel you will burn. Prior to take your fuel, firstly try by taking sample and afterwards buy it. The coals with high calorie may damage casting and sheet metal materials. Do not use pulverized coal, wet coal and coke coal.
INFORMATION ON ASSEMBLY
The device should not be mounted to the places that come into contact with water or that are extremely humid.
If the device is mounted to the places like garden in open or outdoor environment, a sheltered environment should be ensured (it should be protected from effects of outdoor environment such as rain and sun).
The device should be mounted to the sites where it can get enough air for proper combustion.
The device should be mounted as appropriate to control and service intervention.
Assemblier company should mount the device in accordance with all of the instructions and warnings specified in this booklet. Otherwise, the company that carries out assembly will be held responsible for problems that may arise.
Installment, hot water, flue connections passing through external environments should be definitely insulated.
Flue is one of the most significant elements of the system. Where there is no a good flue, a good combustion and efficiency will not happen.
The installment should be pulled starting from the outside dimensions of the device and getting smaller, however dimension of installment should not be reduced from 3/4” to the last radiator group.
The water inlet and outlet connections of radiators should be made transversely.
Air relief cock should be mounted to each radiator group.
An expansion tank which is in compliance with the capacity should be mounted to the top point of installment.
Ball valve should be mounted to outgoing and return lines of the device.
Circulation pump should be mounted to the outgoing and return line in a way to press to boiler.
Impermeability of flue connections should be absolutely ensured.
The connections of flue should be made in outlet dimensions of the device and flue section should not be narrowed down.
Earth connections of the device should be made definitely.
The device should not be exposed to voltage fluctuation.
Due to the electricity and earth connections of the device is not made according to the rules; YAĞMUR TEKNİK which is manufacturer company cannot be held responsible for damages to people, animals and objects.
If the boiler is mounted in indoor area, there should be definitely a ventilation window.
The boiler should be mounted in its scales and it should be in smooth surface. In central systems it should be placed on the base with a minimum height of 25 cm.
The elements such as valve, check valve filter etc. should not be on safety pipes between boiler and expansion.
Do not ever use your boiler with assembly connected to closed expansion. Warn your assemblier. The system with connection of the closed expansion is definitely not within scope of warranty. The device is accepted as out of warranty. Yağmur Teknik cannot be held responsible for problems arising from the closed expansion.