GENERAL INFORMATION TO BE TAKEN INTO CONSIDERATION
External surface cleaning should not be made by sharp tools or chemicals but with warm water and soap.
For boilers operated with fuel oil, purchase fuel before finishing fuel in storage.
Do not open the doors or keep them open while the fuel is burning in the device.
Do not fill any other fuels other than coal or the fuel advised by the manufacturer (liquid or other inflammable materials) for better burning. Never remove the bunker sleeve.
Use clean fuel. Wet coal or materials like nuts, bolts, stones mixed in the coal might damage the stoker mechanism.
Do not approach your hand or throw strange materials (e.g. stones) while reducer or spiral is running.
Reducer should not be taken into operation before the inflammable materials put on the coal at first burning (wood, firewood, etc.) turns into cinders, unburned materials drop into the spiral part and cause sticking.
Fire should be kept at the upper part of the burning chamber which is called pot. Fire should not burn inside the pot, otherwise it might damage the boiler by melting cast material and the spiral.
In YTPH Type boilers, coal level in the bunker should be at least 20 cm above the ground; otherwise there is a risk of smoke coming from your bunker.
Do not lose the user’s manual, if required apply to the user’s manual.
Boiler efficiency and lifecycle shall improve if you act in compliance with the issues defined in the user’s manual.
Use your boiler which is delivered to you in good an operating conditions after making the relevant set up by our authorized service, according to the explanations made by authorized service and do not change the settings without informing your authorized service.
In YTPH Type boilers, do not throw the fuel into the boiler with melting plastic materials like sucks or bags. Material melting with heat might damage grills or movable parts.
Purchase your fuel before calling the service for first operation.